Add intelligence to your ceiling boxes
Connect to a group of lamps with a total max. of 250W or connect to individual lamps. Dim everything from dimmable LEDs to incandescent light bulbs and control your light sources from the Z-Wave network.
DIMMY can be mounted in a ceiling box or junction box.
Use cable relief. Optionally, use the screw holes to fasten to a surface.
Warning! Only authorised technicians under consideration of the country-specific installation norms may do works with 230 Volt mains power. Prior to the assembly of the product, the voltage network has to be switched off.
Dimmed output (~), Neutral (N) and Line (L) must be connected according to the diagram below. Contacts with same markings (N or L) are internally connected and can be used for cable looping.
Use a cable, max. 2,5 mm², with a stripped length of 9-10 mm. The cable must be solid or closed with a ferrule. Connect the cable by simply pushing it into the connection terminal. Disconnect cables by pressing a slotted screwdriver with 2,5 mm slot against release button while pulling the cable (A)
Add/remove DIMMY to the Z-Wave-network by pressing the center switch (I). The LED will now start blinking.
Restore Factory Settings
Restore factory settings by pressing the center switch (I) for at least 10 seconds.
|DIMENSIONS (HXWXD)||15 mm x 45 mm x 54 mm|
|POWER SUPPLY||100 – 230 V AC|
|POWER CONSUMPTION||Max. 0.8 W / 0.5 W standby|
|CLAMPS||Screwless terminals 0.2 – 2.5 mm² / 24 – 14 AWG|
|CONTACTS||5 poles, 2 x looped line, 2 x looped neutral, 1 load|
|RADIO PROTOCOL||Z-Wave®: EU 868.4MHz – 500 Series|
|RADIO RANGE||40 m indoor / 80 m outdoor|
DS/EN 50491-3:2009 or DS/EN IEC 63044-3:2018
DS/EN 60669-2-1, DS/EN60669-2-1/A1, DS/EN 60669-2-1/A12, DS/EN 60669-2-1/AC:2007, DS/EN 60669-1:2018